View and Download Eaton user manual online. 8–15 kVA. UPS pdf manual download. CAUTION: REFER TO OPERATOR’S MANUAL – Refer to your operator’s manual EATON Powerware® UPS-Mounted Bypass Switch (8–15 kVA) User’s. Features of the Eaton UPS. • A true online Eaton kVa UPS BackUP timES (in minUtES). UPS. (1). (2) .. Please refer to manual for details. 2.
|Published (Last):||7 September 2010|
|PDF File Size:||14.12 Mb|
|ePub File Size:||11.62 Mb|
|Price:||Free* [*Free Regsitration Required]|
All other trademarks are property of their respective companies. No part of this document may be reproduced in any way without the express written approval of Manuall Corporation.
For copies of the EC Declaration of Conformity, contact: Special Symbols The following are examples of symbols used on the UPS or accessories to alert you to important information: With the Eatonyou can safely eliminate the effects of electrical line disturbances and guard the integrity of your systems and mznual.
CAN Bridge Card provides connectivity for system metering and operational mode control.
EATON USER MANUAL Pdf Download.
Keep unauthorized personnel away from batteries. Proper disposal of batteries is required. Refer to your local codes for disposal requirements. Never dispose of batteries in a fire. Batteries may explode when exposed to flame. Ne jamais jeter les batteries au feu. L’exposition aux flammes risque de les faire exploser. Consulte las normas locales para conocer los requisitos pertinentes.
Hang the top edge of the cover on the cabinet first, then lower the bottom edge and snap into place. Unloading the Cabinet With the cabinet supported, slowly pull the pallet away from the cabinet see Figure 5. Removing the Pallet Roll the cabinet to the desired location. Select upe of the following installation options according to your UPS configuration: Switch off utility power to the distribution point where the UPS will be connected. Replace the UPS wiring access cover.
AWG maunal than shown in this table because of temperature, number of conductors in the conduit, or long service runs. Hardwire the input, output, and ground terminations for the input isolation transformer. See Table 2 for specifications and Figure 10 ezton a detailed view of the input isolation transformer terminal block. Code may require a larger AWG size than shown in this table because of temperature, number of conductors in the conduit, or long service runs.
Greenlee punch or similar device see Figure 10 on page Install the supplied edge grommet in the top of the input isolation transformer wiring cover.
Insert the supplied nylon bushing inside the wiring access hole. Remove the lowest top cover screw on each side of the UPS and discard. UPS electronics unit through an access slot. Replace the wiring access cover on the UPS and the optional isolation transformer, if applicable. Remove the six screws from the bypass switch front cover and remove the cover see Figure Remove and discard any packing material from inside the bypass switch. Switch mannual utility power to the distribution point where the bypass switch cabinet and UPS will be connected.
See Figure 26 for a detailed view of the terminal strip label. Signal Cable Installation Replace the bypass switch front cover and the UPS wiring access cover. The stabilizing bracket is optional for 2-high cabinets. Repeat for each additional EBM. Front Ground Strap Figure With wire cutters, cut either side of the tab and twist down to remove the tab see Figure Be sure the cables fit in the access holes in the covers. Reinstalling the Front Covers Rev G www.
Eaton 9155 User Manual
In addition, the LanSafe Power Management Software can be installed and used to communicate with the UPS via one of the serial communication connections. The relay output contacts must not be connected to any utility connected circuits. Reinforced insulation to the utility is required. If active, the UPS knows that input is fed from the generator. Bypass is disabled; the automatic battery test is disabled. External Transformer This option is not used.
Overtemperature Rev G www. Display Functions As the default or after 15 minutes of inactivity, the LCD displays the selectable startup screen. The default is the Eaton logo and can be changed to the Mimic screen in the User Settings menu. The backlit LCD automatically dims after a long period of inactivity. Press any button to restore the screen.
Press and hold the button for three seconds, until the UPS stops beeping. The UPS starts in Battery mode within two minutes and supplies battery power to your equipment.
Switch on utility power where the UPS is connected.
The load is now powered by utility power. Press the button to save the setting. Press the button until the Eaton logo appears. The UPS is disconnected from the batteries and is on logic power only. Switch off utility power where the UPS is connected.
Check the battery recharge date on the shipping carton label. If the date has expired and the batteries were never recharged, do not use the UPS. Contact your service representative. Figure 47 shows a UPS with a separate battery cabinet and a wall-mounted bypass switch.
Step 3; otherwise, power to the load may be lost. Turn the maintenance bypass switch to the UPS position to return to Normal mode. The UPS is now powering the load. UPS with two battery sections 15 kVA, If the condition persists, contact your service representative.
Battery test failed The batteries need service. Please have the following information ready when you call for service: Model number Serial number Firmware version number Date of failure or problem Symptoms of failure or problem Customer return address and contact information Rev G www. The warrantor for the limited warranties set forth herein is Eaton Corporation Inc.
This Guaranty applies even in the event that the Product is initially sold by Company for resale to an End-User. Outside of the USA, contact your local Eaton product sales or service representative. Also See for User manual – 90 pages Reference manual – pages User manual – 66 pages.
Page of 92 Go. Table of Contents Add to my manuals Add. Also See for Eaton Eaton E. Eaton Powerware User Manual 90 pages. Eaton User Manual 68 pages. Powerware series rail kit 9- and slot cabinets 12 pages.
Page 2 Schneider Automation. Special Symbols Special Symbols The following are examples of symbols used on the UPS or accessories to alert you to important information: Introduction With the Eatonyou can safely eliminate the effects of electrical line disturbances and guard the integrity of your systems and equipment.
Safety Warnings Keep unauthorized personnel away from batteries. Page 15 Figure 3. Page 16 Figure 4. Ups Terminal Block Wiring AWG size than shown in this table because of temperature, number of conductors in the conduit, or long service runs. Page 26 Greenlee punch or similar device see Figure 10 on page Page 32 UPS electronics unit through an access slot. Page 33 Step 1. Page 37 Replace the wiring access cover on the UPS and the optional isolation transformer, if applicable.
Wall-mounted Bypass Switch Installation Wall-mounted Bypass Switch Setup Remove the six screws from the bypass switch front cover and remove the cover see Figure Page 44 See Figure 26 for a detailed view of the terminal strip label. Page 45 AWG size than shown in this table because of temperature, number of conductors in the conduit, or long service runs. Installing Communication Options And Control Terminals With wire cutters, cut either side of the tab and twist down to remove the tab see Figure